Designed to prevent the presence of electromagnetic fields in rest areas (bedrooms etc) by switching the installation phase off when there is no power demand.
The installation phase will remain switched off while the main loads are off.
When a main load is switched on (lamps or radio etc), the relay will switch the phase back on to allow normal installation operation.
|Voltage rating ||230 Va.c.|
|Breaking power ||16 A / 250 Va.c., cosφ=1|
|Breaking sensitivity ||5 to 200 mA|
|Control voltage ||5 - 230 Vd.c. programmable|
| || |
|GLE 12-3 ||Accesory for special loads|
Documentation and downloads